Accession Number : ADA310959
Title : Control Efficiency Determination of Sudden Expansion Incinerator Bldg 348, Kelly AFB, Texas.
Descriptive Note : Final rept. 19 Jul 95-11 Jan 96,
Corporate Author : ARMSTRONG LAB BROOKS AFB TX OCCUPATIONAL AND ENVIRONMENTAL HEALTH DIRECTORATE
Personal Author(s) : O'Brien, Robert J.
PDF Url : ADA310959
Report Date : JUN 1996
Pagination or Media Count : 128
Abstract : Compliance emissions testing and Volatile Organic Compound (VOC) destruction efficiency determination were conducted on the Sudden Expansion (SUE) Incinerator located at the Kelly AFB Fuel Accessory Test Facility, Bldg 348. Compliance standards and requirements are found in Operating Permit No. 6493, as amended/renewed by the State of Texas on 24 March 1994. The purpose of the Kelly AFB SUE Incinerator is to destroy calibration fluid vapors emitted from fuel accessory test stands located in Bldg 348. The incinerator can also be used to destroy liquid waste calibration fluid by burning it as a supplemental fuel. Emissions testing was conducted during combustion of both vapors and liquid calibration fluid. For purposes of determining the incinerator VOC destruction efficiency, monitoring for Total VOC concentration in the inlet air stream was conducted on 19-20 July 1995. Emissions testing of the incinerator exhaust was conducted on 10-11 January 1996 and included monitoring for Total VOC, oxides of nitrogen (NOx), carbon monoxide (CO), and visible emissions. Results indicate that the SUE Incinerator is in compliance with all applicable emission standards and with the VOC destruction efficiency requirement.
Descriptors : *EMISSION, *ORGANIC COMPOUNDS, *VOLATILITY, *AIR FORCE FACILITIES, *INCINERATORS, *TEST FACILITIES, TEST AND EVALUATION, CONTROL, REQUIREMENTS, VAPORS, DESTRUCTION, AIR FLOW, EFFICIENCY, COMBUSTION, FUELS, VISIBILITY, STANDARDS, FLUIDS, CALIBRATION, EXPANSION, CARBON MONOXIDE, NITROGEN OXIDES, DETERMINATION, INLETS, TEXAS, LIQUID WASTES, TEST STANDS.
Subject Categories : Organic Chemistry
Solid Wastes Pollution and Control
Distribution Statement : APPROVED FOR PUBLIC RELEASE